Q1: What is the power consumption of the UC1114?
Answer: When UC1114 send Lora message, the highest power consumption is 0.24W.
Q2: Do you have a UC controller that can accept a BACnet MSTP input?
Answer: No, Milesight controllers can not compatible this input yet.
What does “UC50x only starts counting when it detects 6 pules from pulse device” mean?
If restarting UC502, how does the pulse count?
For hardware 1.x UC50x series devices, when it receive within 5 pulses, the device will only detect pulse counter as 0; when it receive 6 pulses, the device will detect pulse counter as 6.
The counts will accumulate after restarting, but if you click Clear button on GPIO Setting -> Pulse Counter of UC502, it will reset the counter then again ignore the first 5 counters.
Q4: Can I use GPIO interface of UC51X to read DI status?
Answer: No, GPIO interfaces are fixed as pulse counter type.
Q5: May I know if Milesight have LoRaWAN controller with 4 DI & 4 DO or more?
Answer: No, the UC1114 has at most 2 DI and 2 DO interfaces. It’s suggested to use two UC1114 devices.